# AF1-099 Transition Sort Retool Results -- Reprioritized to Transition Cycle #1

##### v1.00 released 2023-12-14 11:12

### Moshannon-Milesburg 230 kV III

### 75.9 MW Capacity / 126.5 MW Energy

#### Introduction

In accordance with Tariff Part VII, Subpart B, section 304, PJM performed load flow analysis (Transition Sort Retool) on all AE1 through AG1 projects that have met eligibility requirements according to Tariff, Part VII, Subpart B, section 303. The purpose of this study is to determine whether a project would be classified as eligible for the Expedited Process (Fast Lane) or if it would be reprioritized to be studied as part of Transition Cycle #1 (TC1) using the criteria from the Expedited Process Eligibility section of Tariff Part VII, section 304. This is not a System Impact Study report.

Below are the results of the study, details of how the study was performed, criterion used in the evaluation of the Expedited Process vs. TC1 determination, and next steps in the interconnection process for your project.

## Transition Cycle #1:

The AF1-099 project has not met the Expedited Process Eligibility requirements in Tariff Part VII, Subpart B, section 304 and will therefore be reprioritized to Transition Cycle #1. Please see "Transition Cycle #1 Rules" below.

### Transition Sort Retool Study Process and Criteria:

In order to determine Expedited Process vs. Transition Cycle #1 classification, projects which met the Transition Eligibility requirements from Tariff Part VII, Subpart B, section 303 were studied on the base case model that was used for the original System Impact Study analysis. Both a summer peak and light load load flow analysis were performed. Projects that have cost allocation eligibility or are identified as the first to cause a system violation which requires the need for a Network Upgrade with a total estimated cost greater than $5 million will be reprioritized to Transition Cycle #1. All other projects will be eligible for the expedited procedures set forth in Tariff Part VII, Subpart B, section 304 (B).

Expedited Process Eligibility: OATT Tariff Part VII, section 304:

A project is not eligible for the expedited process if it has cost allocation eligibility or is identified as the first to cause, as determined according to Tariff, Part VI, section 217.3, for a Network Upgrade which has a total estimated cost of greater than $5,000,000. Such cost estimate will be based on Transmission Provider's most recently available data.

Not considered in the Transition Sorting: The cost of the Interconnection Facilities is not considered when determining a project's eligibility for the expedited process. Affected Systems upgrade costs are also not considered in the evaluation.

## Transition Sort Retool Results Provided:

This report includes a list of:

- the overloaded flowgates (overloaded facilities + contingency pair) that the project contributes towards
- other interconnection projects that may also contribute to the overloaded facility, and
- the total estimated cost for any required Network Upgrades.

## Important Notes:

Note for Uprate Projects: Per Tariff Part VII, Subpart B, section 304 (B), if a project is an uprate (project relies on the Interconnection Facilities of a prior project) whose base project does not qualify for the expedited process, the uprate also will not qualify for the expedited process, regardless of analysis results.

Notes regarding Results displayed:

- Some flowgate overloads that a New Service Request contributes to, but does not contribute enough to meet cost allocation eligibility (per Manual 14A, Attachment B.3), may be reported in this Transition Sort report. These types of flowgates do not affect the classification of the New Service Request as either Expedited Process or Transition Cycle #1 because cost allocation eligibility has not been met.
- For projects that were determined to not meet Expedited Process eligibility and are being reprioritized to Transition Cycle #1, not all reinforcements in excess of $5,000,000 may be shown in this report. This report may only display a subset of those reinforcements determined to be in excess of $5,000,000 which would classify the project as not meeting Expedited Process Eligibility. This is not a formal System Impact Study.

## Next Steps for your project:

### Transition Cycle #1 Rules:

Refer to Tariff Part VII, Subpart B, section 304 (C) for the Transition Cycle #1 Project Rules.

Transition Cycle #1 will start no later than one year from the Transition Start Date (July 10, 2023). Transition Cycle #1 will run simultaneously with the expedited process, however Transition Cycle #1, Phase III will not begin until all expedited process projects have been completed.

Projects that are reprioritized to Transition Cycle #1 will not need to re-apply to the Interconnection Cycle Process. Therefore, there is no Application Review Phase for Transition Cycle #1. The cycle process for Transition Cycle #1 includes three Study Phases and three Decision Points:

- Phase I System Impact Study and Decision Point I; and
- Phase II System Impact Study and Decision Point II; and
- Phase III System Impact Study and Decision Point III

Refer to Tariff Part VII, Subpart D, section 307 for the Transition Cycle #1 study process.

#### General

The Interconnection Customer (IC), has proposed a Solar; Storage generating facility located in the APS zone — Clearfield County, Pennsylvania. The installed facilities will have a total capability of 126.5 MW with 75.9 MW of this output being recognized by PJM as Capacity.

Project Information | |
---|---|

Queue Number | AF1-099 |

Project Name | Moshannon-Milesburg 230 kV III |

Developer Name | Moonlight Flats Solar Power, LLC |

State | Pennsylvania |

County | Clearfield |

Transmission Owner | APS |

MFO | 126.5 MW |

MWE | 126.5 MW |

MWC | 75.9 MW |

Fuel Type | Solar; Storage |

Basecase Study Year | 2023 |

#### Point of Interconnection

AF1-099 will interconnect with the APS transmission system by tapping the Moshannon to Milesburg 230kV line.

The interconnection of the project AF1-099 will be accomplished by constructing a new 230 kV three (3) breaker ring bus substation and looping the Moshannon to Milesburg 230kV line into the new station. The IC will be responsible for acquiring all easements, properties, and permits that may be required to construct both the new interconnection switching station and the associated facilities. The IC will also be responsible for the rough grade of the property and an access road to the proposed three breaker ring bus site. The project will also require non-direct connection upgrades at the remote end substations.

#### Summer Peak Analysis

The Queue Project was evaluated as a 126.5 MW (Capacity 75.9 MW) injection in the APS area. Project was evaluated for compliance with applicable reliability planning criteria (PJM, NERC, NERC Regional Reliability Councils, and Transmission Owners). Potential Summer peak period network impacts are listed below:

Important to Note:

Note for Uprate Projects: Per Tariff Part VII, Subpart B, section 304 (B), if a project is an uprate (project relies on the Interconnection Facilities of a prior project) whose base project does not qualify for the expedited process, the uprate also will not qualify for the expedited process, regardless of analysis results.

Notes regarding Results displayed:

- Some flowgate overloads that a New Service Request contributes to, but does not contribute enough to meet cost allocation eligibility (per Manual 14A, Attachment B.3), may be reported in this Transition Sort report. These types of flowgates do not affect the classification of the New Service Request as either Expedited Process or Transition Cycle #1 because cost allocation eligibility has not been met.
- For projects that were determined to not meet Expedited Process eligibility and are being reprioritized to Transition Cycle #1, not all reinforcements in excess of $5,000,000 may be shown in this report. This report may only display a subset of those reinforcements determined to be in excess of $5,000,000 which would classify the project as not meeting Expedited Process Eligibility. This is not a formal System Impact Study.

Summer Peak Analysis | |||||||||||
---|---|---|---|---|---|---|---|---|---|---|---|

Area | Facility Description | Contingency Name | Contingency Type | DC|AC | Initial Loading | Final Loading | Rating (MVA) | Rating Type | MVA to Mitigate | MW Contribution | |

PENELEC |
26GLADE-26WARREN 230.0 kV Ckt 1 line
200593 to 200811 ckt 1 |
PN-P2-3-PN-345-003A-B10
CONTINGENCY 'PN-P2-3-PN-345-003A-B10' DISCONNECT BRANCH FROM BUS 200826 TO BUS 200595 CKT 1 /*26HANDSMLK 345.0 - 26WAYNE 345.0 OPEN BRANCH FROM BUS 200598 TO BUS 200595 CKT 2 /*26WAYNE 115.0 - 26WAYNE 345.0 END |
Breaker | AC | 98.09 % | 100.25 % | 666.0 | B | 667.66 | 14.76 | |

PENELEC |
26GLADE-26WARREN 230.0 kV Ckt 1 line
200593 to 200811 ckt 1 |
PN-P2-3-PN-345-003A-B45
CONTINGENCY 'PN-P2-3-PN-345-003A-B45' DISCONNECT BRANCH FROM BUS 200826 TO BUS 200595 CKT 1 /*26HANDSMLK 345.0 - 26WAYNE 345.0 OPEN BRANCH FROM BUS 200598 TO BUS 200595 CKT 1 /*26WAYNE 115.0 - 26WAYNE 345.0 END |
Breaker | AC | 98.05 % | 100.21 % | 666.0 | B | 667.4 | 14.75 |

Details for 26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | |||||
---|---|---|---|---|---|

Monitored Fac/Ctg | Bus # | Bus Name | Type | Full MW Contribution | GenDeliv MW Contribution |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 936991 | AD2-133 C | Adder | 1.26 MW | 1.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 936992 | AD2-133 E | Adder | 5.75 MW | 4.88 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942351 | AE2-248 C | Adder | 0.91 MW | 0.77 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942352 | AE2-248 E | Adder | 0.61 MW | 0.52 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942491 | AE2-262 C | 50/50 | 5.56 MW | 5.56 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942492 | AE2-262 E | 50/50 | 3.73 MW | 3.73 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942501 | AE2-263 C | 50/50 | 5.22 MW | 5.22 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942502 | AE2-263 E | 50/50 | 3.49 MW | 3.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942961 | AE2-316 C | 50/50 | 4.2 MW | 4.2 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942962 | AE2-316 E | 50/50 | 4.98 MW | 4.98 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944311 | AF1-099 C | 50/50 | 8.86 MW | 8.86 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944312 | AF1-099 E | 50/50 | 5.9 MW | 5.9 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944321 | AF1-100 C | 50/50 | 18.22 MW | 18.22 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944322 | AF1-100 E | 50/50 | 12.15 MW | 12.15 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944471 | AF1-112 C | Adder | 0.85 MW | 0.72 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944472 | AF1-112 E | Adder | 0.58 MW | 0.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944771 | AF1-142 C | 50/50 | 14.17 MW | 14.17 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944772 | AF1-142 E | 50/50 | 9.45 MW | 9.45 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944881 | AF1-153 C O1 | 50/50 | 1.62 MW | 1.62 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944882 | AF1-153 E O1 | 50/50 | 1.08 MW | 1.08 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944901 | AF1-155 C | 50/50 | 1.61 MW | 1.61 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944902 | AF1-155 E | 50/50 | 1.07 MW | 1.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 945121 | AF1-177 | Adder | -2.69 MW | -2.28 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 945161 | AF1-181 | 50/50 | 0.36 MW | 0.36 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 945171 | AF1-182 | 50/50 | 0.49 MW | 0.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 945181 | AF1-183 | 50/50 | 0.12 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 945331 | AF1-198 | Adder | 0.19 MW | 0.16 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200642 | 26SENECA#1 | 50/50 | 14.8 MW | 14.8 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200643 | 26SENECA#2 | 50/50 | 13.98 MW | 13.98 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200644 | 26SENECA#3 | 50/50 | 1.32 MW | 1.32 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200649 | 26PENNTECH | 50/50 | 1.41 MW | 1.41 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200665 | 26SHAWVL 3 | 50/50 | 3.84 MW | 3.84 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200666 | 26SHAWVL 4 | 50/50 | 3.82 MW | 3.82 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200715 | 26SHAWVL 1 | 50/50 | 2.63 MW | 2.63 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200722 | 26SHAWVL 2 | 50/50 | 2.69 MW | 2.69 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200894 | 26K02 | Adder | 4.47 MW | 3.8 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 200913 | 26SHAW-D | 50/50 | 0.12 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 203349 | 26Z1-069 C | 50/50 | 0.28 MW | 0.28 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 203999 | P-047 E | Adder | 5.55 MW | 4.71 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 235003 | AC1-025 E | Adder | 0.14 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 236828 | 01GRAYMONT | Adder | 0.39 MW | 0.33 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 916202 | Z1-069 E | 50/50 | 6.41 MW | 6.41 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940201 | AE2-001 C | Adder | 1.17 MW | 0.99 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940202 | AE2-001 E | Adder | 0.78 MW | 0.66 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940681 | AE2-055 C | Adder | 1.12 MW | 0.95 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940682 | AE2-055 E | Adder | 0.74 MW | 0.63 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940861 | AE2-074 C | 50/50 | 2.23 MW | 2.23 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 940862 | AE2-074 E | 50/50 | 2.93 MW | 2.93 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941191 | AE2-113 C | 50/50 | 10.93 MW | 10.93 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941192 | AE2-113 E | 50/50 | 10.26 MW | 10.26 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941271 | AE2-121 C | Adder | 0.62 MW | 0.53 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941272 | AE2-121 E | Adder | 0.42 MW | 0.35 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941321 | AE2-126 C | 50/50 | 0.26 MW | 0.26 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941322 | AE2-126 E | 50/50 | 1.17 MW | 1.17 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941332 | AE2-129 E | Adder | 0.76 MW | 0.64 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941351 | AE2-131 C | Adder | 1.13 MW | 0.96 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 941352 | AE2-131 E | Adder | 0.76 MW | 0.64 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946111 | AF1-276 C | 50/50 | 15.02 MW | 15.02 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946112 | AF1-276 E | 50/50 | 7.4 MW | 7.4 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946121 | AF1-277 C | 50/50 | 15.02 MW | 15.02 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946122 | AF1-277 E | 50/50 | 7.4 MW | 7.4 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946131 | AF1-278 C | 50/50 | 11.97 MW | 11.97 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946132 | AF1-278 E | 50/50 | 5.95 MW | 5.95 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946381 | AF1-302 C | 50/50 | 1.84 MW | 1.84 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 946382 | AF1-302 E | 50/50 | 2.45 MW | 2.45 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 290086 | Q-036 E | Adder | 3.2 MW | 2.72 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944691 | AF1-134 C O1 | Adder | 0.96 MW | 0.82 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944692 | AF1-134 E O1 | Adder | 0.64 MW | 0.55 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 923442 | AB1-160 C | 50/50 | 0.08 MW | 0.08 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 923443 | AB1-160 E | 50/50 | 1.83 MW | 1.83 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 942813 | AE2-299 BAT | 50/50 | 29.67 MW | 29.67 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | 944392 | AF1-104 BAT | 50/50 | 3.1 MW | 3.1 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | NEWTON | LTFEXP_NEWTON->LTFIMP_NEWTON | CLTF | 1.44 MW | 1.44 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | BLUEG | LTFEXP_BLUEG->LTFIMP_BLUEG | CLTF | 2.3 MW | 2.3 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | G-007A | LTFEXP_G-007A->LTFIMP_G-007A | CLTF | 4.13 MW | 4.13 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | VFT | LTFEXP_VFT->LTFIMP_VFT | CLTF | 11.31 MW | 11.31 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | PRAIRIE | LTFEXP_PRAIRIE->LTFIMP_PRAIRIE | CLTF | 3.35 MW | 3.35 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | COFFEEN | LTFEXP_COFFEEN->LTFIMP_COFFEEN | CLTF | 0.27 MW | 0.27 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | CHEOAH | LTFEXP_CHEOAH->LTFIMP_CHEOAH | CLTF | 0.51 MW | 0.51 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | EDWARDS | LTFEXP_EDWARDS->LTFIMP_EDWARDS | CLTF | 0.49 MW | 0.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | TILTON | LTFEXP_TILTON->LTFIMP_TILTON | CLTF | 0.88 MW | 0.88 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | MADISON | LTFEXP_MADISON->LTFIMP_MADISON | CLTF | 0.05 MW | 0.05 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | GIBSON | LTFEXP_GIBSON->LTFIMP_GIBSON | CLTF | 0.74 MW | 0.74 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | CALDERWOOD | LTFEXP_CALDERWOOD->LTFIMP_CALDERWOOD | CLTF | 0.51 MW | 0.51 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | FARMERCITY | LTFEXP_FARMERCITY->LTFIMP_FARMERCITY | CLTF | 0.07 MW | 0.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | TRIMBLE | LTFEXP_TRIMBLE->LTFIMP_TRIMBLE | CLTF | 0.74 MW | 0.74 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B10 | CATAWBA | LTFEXP_CATAWBA->LTFIMP_CATAWBA | CLTF | 0.28 MW | 0.28 MW |

Details for 26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | |||||
---|---|---|---|---|---|

Monitored Fac/Ctg | Bus # | Bus Name | Type | Full MW Contribution | GenDeliv MW Contribution |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 936991 | AD2-133 C | Adder | 1.25 MW | 1.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 936992 | AD2-133 E | Adder | 5.74 MW | 4.88 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942351 | AE2-248 C | Adder | 0.91 MW | 0.77 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942352 | AE2-248 E | Adder | 0.61 MW | 0.52 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942491 | AE2-262 C | 50/50 | 5.55 MW | 5.55 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942492 | AE2-262 E | 50/50 | 3.73 MW | 3.73 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942501 | AE2-263 C | 50/50 | 5.22 MW | 5.22 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942502 | AE2-263 E | 50/50 | 3.49 MW | 3.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942961 | AE2-316 C | 50/50 | 4.2 MW | 4.2 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942962 | AE2-316 E | 50/50 | 4.97 MW | 4.97 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944311 | AF1-099 C | 50/50 | 8.85 MW | 8.85 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944312 | AF1-099 E | 50/50 | 5.9 MW | 5.9 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944321 | AF1-100 C | 50/50 | 18.21 MW | 18.21 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944322 | AF1-100 E | 50/50 | 12.14 MW | 12.14 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944471 | AF1-112 C | Adder | 0.85 MW | 0.72 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944472 | AF1-112 E | Adder | 0.58 MW | 0.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944771 | AF1-142 C | 50/50 | 14.16 MW | 14.16 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944772 | AF1-142 E | 50/50 | 9.44 MW | 9.44 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944881 | AF1-153 C O1 | 50/50 | 1.62 MW | 1.62 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944882 | AF1-153 E O1 | 50/50 | 1.08 MW | 1.08 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944901 | AF1-155 C | 50/50 | 1.61 MW | 1.61 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944902 | AF1-155 E | 50/50 | 1.07 MW | 1.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 945121 | AF1-177 | Adder | -2.69 MW | -2.28 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 945161 | AF1-181 | 50/50 | 0.36 MW | 0.36 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 945171 | AF1-182 | 50/50 | 0.48 MW | 0.48 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 945181 | AF1-183 | 50/50 | 0.12 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 945331 | AF1-198 | Adder | 0.19 MW | 0.16 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200642 | 26SENECA#1 | 50/50 | 14.8 MW | 14.8 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200643 | 26SENECA#2 | 50/50 | 13.98 MW | 13.98 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200644 | 26SENECA#3 | 50/50 | 1.32 MW | 1.32 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200649 | 26PENNTECH | 50/50 | 1.41 MW | 1.41 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200665 | 26SHAWVL 3 | 50/50 | 3.84 MW | 3.84 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200666 | 26SHAWVL 4 | 50/50 | 3.82 MW | 3.82 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200715 | 26SHAWVL 1 | 50/50 | 2.63 MW | 2.63 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200722 | 26SHAWVL 2 | 50/50 | 2.69 MW | 2.69 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200894 | 26K02 | Adder | 4.46 MW | 3.79 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 200913 | 26SHAW-D | 50/50 | 0.12 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 203349 | 26Z1-069 C | 50/50 | 0.28 MW | 0.28 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 203999 | P-047 E | Adder | 5.54 MW | 4.71 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 235003 | AC1-025 E | Adder | 0.14 MW | 0.12 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 236828 | 01GRAYMONT | Adder | 0.39 MW | 0.33 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 916202 | Z1-069 E | 50/50 | 6.41 MW | 6.41 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940201 | AE2-001 C | Adder | 1.17 MW | 0.99 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940202 | AE2-001 E | Adder | 0.78 MW | 0.66 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940681 | AE2-055 C | Adder | 1.12 MW | 0.95 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940682 | AE2-055 E | Adder | 0.74 MW | 0.63 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940861 | AE2-074 C | 50/50 | 2.23 MW | 2.23 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 940862 | AE2-074 E | 50/50 | 2.93 MW | 2.93 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941191 | AE2-113 C | 50/50 | 10.92 MW | 10.92 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941192 | AE2-113 E | 50/50 | 10.25 MW | 10.25 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941271 | AE2-121 C | Adder | 0.62 MW | 0.53 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941272 | AE2-121 E | Adder | 0.42 MW | 0.35 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941321 | AE2-126 C | 50/50 | 0.26 MW | 0.26 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941322 | AE2-126 E | 50/50 | 1.17 MW | 1.17 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941332 | AE2-129 E | Adder | 0.76 MW | 0.64 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941351 | AE2-131 C | Adder | 1.13 MW | 0.96 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 941352 | AE2-131 E | Adder | 0.76 MW | 0.64 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946111 | AF1-276 C | 50/50 | 15.02 MW | 15.02 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946112 | AF1-276 E | 50/50 | 7.4 MW | 7.4 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946121 | AF1-277 C | 50/50 | 15.02 MW | 15.02 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946122 | AF1-277 E | 50/50 | 7.4 MW | 7.4 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946131 | AF1-278 C | 50/50 | 11.97 MW | 11.97 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946132 | AF1-278 E | 50/50 | 5.95 MW | 5.95 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946381 | AF1-302 C | 50/50 | 1.83 MW | 1.83 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 946382 | AF1-302 E | 50/50 | 2.44 MW | 2.44 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 290086 | Q-036 E | Adder | 3.19 MW | 2.71 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944691 | AF1-134 C O1 | Adder | 0.96 MW | 0.82 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944692 | AF1-134 E O1 | Adder | 0.64 MW | 0.54 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 923442 | AB1-160 C | 50/50 | 0.08 MW | 0.08 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 923443 | AB1-160 E | 50/50 | 1.83 MW | 1.83 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 942813 | AE2-299 BAT | 50/50 | 29.65 MW | 29.65 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | 944392 | AF1-104 BAT | 50/50 | 3.1 MW | 3.1 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | NEWTON | LTFEXP_NEWTON->LTFIMP_NEWTON | CLTF | 1.44 MW | 1.44 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | BLUEG | LTFEXP_BLUEG->LTFIMP_BLUEG | CLTF | 2.3 MW | 2.3 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | G-007A | LTFEXP_G-007A->LTFIMP_G-007A | CLTF | 4.13 MW | 4.13 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | VFT | LTFEXP_VFT->LTFIMP_VFT | CLTF | 11.31 MW | 11.31 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | PRAIRIE | LTFEXP_PRAIRIE->LTFIMP_PRAIRIE | CLTF | 3.35 MW | 3.35 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | COFFEEN | LTFEXP_COFFEEN->LTFIMP_COFFEEN | CLTF | 0.27 MW | 0.27 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | CHEOAH | LTFEXP_CHEOAH->LTFIMP_CHEOAH | CLTF | 0.51 MW | 0.51 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | EDWARDS | LTFEXP_EDWARDS->LTFIMP_EDWARDS | CLTF | 0.49 MW | 0.49 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | TILTON | LTFEXP_TILTON->LTFIMP_TILTON | CLTF | 0.87 MW | 0.87 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | MADISON | LTFEXP_MADISON->LTFIMP_MADISON | CLTF | 0.05 MW | 0.05 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | GIBSON | LTFEXP_GIBSON->LTFIMP_GIBSON | CLTF | 0.73 MW | 0.73 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | CALDERWOOD | LTFEXP_CALDERWOOD->LTFIMP_CALDERWOOD | CLTF | 0.51 MW | 0.51 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | FARMERCITY | LTFEXP_FARMERCITY->LTFIMP_FARMERCITY | CLTF | 0.07 MW | 0.07 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | TRIMBLE | LTFEXP_TRIMBLE->LTFIMP_TRIMBLE | CLTF | 0.74 MW | 0.74 MW |

26GLADE-26WARREN 230.0 kV Ckt 1 line l/o PN-P2-3-PN-345-003A-B45 | CATAWBA | LTFEXP_CATAWBA->LTFIMP_CATAWBA | CLTF | 0.28 MW | 0.28 MW |

#### Light Load Analysis

The Queue Project was evaluated as a 126.5 MW (Capacity 75.9 MW) injection in the APS area. Project was evaluated for compliance with applicable reliability planning criteria (PJM, NERC, NERC Regional Reliability Councils, and Transmission Owners). Potential light load period network impacts are listed below:

Important to Note:

Note for Uprate Projects: Per Tariff Part VII, Subpart B, section 304 (B), if a project is an uprate (project relies on the Interconnection Facilities of a prior project) whose base project does not qualify for the expedited process, the uprate also will not qualify for the expedited process, regardless of analysis results.

Notes regarding Results displayed:

- Some flowgate overloads that a New Service Request contributes to, but does not contribute enough to meet cost allocation eligibility (per Manual 14A, Attachment B.3), may be reported in this Transition Sort report. These types of flowgates do not affect the classification of the New Service Request as either Expedited Process or Transition Cycle #1 because cost allocation eligibility has not been met.
- For projects that were determined to not meet Expedited Process eligibility and are being reprioritized to Transition Cycle #1, not all reinforcements in excess of $5,000,000 may be shown in this report. This report may only display a subset of those reinforcements determined to be in excess of $5,000,000 which would classify the project as not meeting Expedited Process Eligibility. This is not a formal System Impact Study.

*(No impacts were found for this analysis)*

#### System Reinforcements

The table below lists all network upgrades which resolve the identified overloaded facilities in this report.

Important to Note:

Notes regarding Results displayed:

- Reinforcements previously identified by Transmission Owners for violations on lower voltage facilities are included in this report. Transmission Owner analysis will be updated as part of the Expedited Process and Transition Cycle 1 retools.

System Reinforcements | |||
---|---|---|---|

RTEP ID | Title | Total Cost | |

n6855.1 | Replace substation conductor at Warren and Glade substations | $350,000 | |

n6855.2 | Rebuild 11.53 miles of transmission line between Warren and Glade. | $42,390,000 |

#### Attachments

#### Conclusion

The Transition Sort load flow retool results indicate that AF1-099 is not eligible for the Expedited Process per PJM Tariff Part VII, Subpart B, section 304 (A) will be reprioritized to Transition Cycle #1. See next steps for your project in the "Introduction" section above.